In a one-pipe heating application, hot water typically enters the system at the top of the building and is distributed down through the pipe, heating up radiators one after the other. However, if one radiator is closed, the water is by-passed between the flow and return pipe leading to increased return temperatures and a lower Delta T. This results in increased return water temperature, which may prevent condensing boilers from opperating efficiently and, on district heating schemes, substantial fines from the heating plant to the building's owner.
Changing the main pump in the system to a Delta T controlled Grundfos TPE pump is the first step. However, there is still no guarantee that a building's inhabitants who are furthest away from the pump will actually receive the heat they require. Grundfos therefore includes a sensor on the system's critical spot to monitor and control the Delta P – the difference between pressure (deliver) and suction (income). This combined solution secures optimum operation in terms of economy, and at the same time delivers the right comfort for occupants.
Delta T control with the TPE3
See how the TPE3 with integrated Delta T control takes charge of a system's need for flow, ensuring increased efficiency and lower energy consumption.
The intelligent solution: multiple control modes
By utilising sensors and multiple control modes in one Grundfos pump solution, you can ensure your system never underperforms. The TPE3 measures and compares the temperature of both the flow and return pipes. At the same time, differential pressure is measured at the system’s critical spot, which is furthest away. This way you not only secure optimal economy by measuring Delta T, but you also secure occupant comfort by measuring Delta P. Together, this ensures you have complete control of Delta T.
Interested in more intelligent application solutions?
Without the optimum return temperature, non-condensing boilers are at the risk of corrosion, thermal shock and breakdowns. Learn how to configure and control boilers the intelligent way with added temperature sensors.
The aim of water boosters is simple: deliver appropriate pressure at all floors. Solutions vary greatly in design and efficiency but zone divided boosters ensure no more pressure is added to the system than what is needed.
Without minimum flow, chilled water systems are susceptible to freezing and tripping. Find out how intelligently controlled variable flow and reduced system complexity can ensure optimum performance.
Whatever your query is, we can help you find the right contact for your local sales company or service centre, as well as our corporate, communications and purchase teams.